Mr. Value Electricians has provided the electrical services for Suwanee GA—from ceiling fan installation to breaker box replacement, electrical shorts, and landscape lighting —for years.
Call us now at: (770) 894-1566 or check out why your neighbors rely on us to deliver electrical services at great value for a fair price in Suwanee GA.
for Suwanee, GA
Our Reviews by City
Anthony - Suwanee, GA 30024
Mr.Value Electrician Cole Jones did a great job finding the issue and helped us out on the weekend when we lost power on a subpanel. Professional Service and flexibility was appreciated by Cole and efficient work effort. Thanks
Dan - Suwanee, GA 30024
John was very thorough, patient, and courteous
Cole displayed and followed thru with 1st class professionalism. All to code. Thanks Clay.
Max - Suwanee, GA 30024
Hanna - Suwanee, GA 30024
Paul - Suwanee, GA 30024
Clay was great! Fast service, efficient, & very professional.
Debbie - Suwanee, GA 30024
Cole was here today and fixed several issues with buzzing blinking lights. Very polite, personable and professional.
Will did a great Job!
Elbert - Suwanee, GA 30024
Will did a great job! He answered our questions, did the work professionally and cleaned up when he finished. He was a great representative for Mr. Value and told me how happy he was to work there. Best thing, we would never have know how nice recessed lights would be, if he had not suggested them on a previous job. I respect folks that take the initiative and suggest things that help me and their company.
Colin - Suwanee, GA 30024
I found Mr. Value Electricians via NextDoor. They came highly recommended and I can see why. I was able to book an appointment the next day. The work was done the same day at a fair price. The service was friendly as well. I would absolutely use Mr. Value again.
Friendly and professional
Jay - Suwanee, GA 30024
Cole arrived early and communicated very well prior to arriving. He was very professional and easy to talk to while providing a diligent service.
Chet - Suwanee, GA 30024
Clay the electrician did a great job on multiple projects to prep a house for sale. Appointment process was friendly and easy.
Erin - Suwanee, GA 30024
Victor - Suwanee, GA 30024
Explained everything, showed what he was doing, very friendly and knowledgeable. Thanks Will!
Mr. Jones went beyond the call of duty..we are very pleased! I would recommend him and your company to anyone!
Steve - Suwanee, GA 30024
Great service, on time and friendly
Scott - Suwanee, GA 30024
Cassie - Suwanee, GA 30024
Clay was fast, professional, and very knowledgeable.
Electrician diagnosed and repaired landscape lighting by replacing the low voltage transformer, GFCI outlets and rewiring the light fixtures
Troubleshooting upstairs bedroom having no power. Found a loose connection on an outlet preventing power on rest of circuit. Replaced with new outlet and bedroom circuit is now working properly.
Diagnosing kitchen light
Tech John replaced chandelier in foyer, replaced 3 garage lights, and replaced a light bulb in a garage door opener as a courtesy.
Tech John diagnosed issue with washer not having power. The issue was determined to be a loose connection on a neutral wire termination causing the wire to melt. The receptacle was replaced, the wire was trimmed back to fresh copper, and the connections were remade. Power was restored, and the circuit was tested and verified to be operating properly after repair.
Tech John installed new ceiling fan at existing location in living room.
Installed whole home surge protector EATON surge protector
Emergency replace main breaker
Trouble shoot and install switch leg
Installing disconnect for air conditioning
Tech John replaced customer-supplied chandelier in foyer area and quoted additional work to do in the future.
-installed wiring from existing garage door opener outlet for a new GFCI outlet near sprinkler control box -installed wiring for a new flood light on back patio off of existing flood light switch leg -installed 3 customer supplied flood lights
Trouble shoot kitchen circuit
- installed a customer supplied chandelier over the basement patio bar on existing wiring - replaced an outdoor GFCI outlet and box with a new box and weather resistant GFCI outlet and bubble cover - Existing GFCI outlet had melted and melted the box as well
Trouble shoot piano room circuit
Homeowner wanted to be able to plug in grill monitor and LED string lights on back deck but had no outlets close enough. Tech John installed 2 new receptacles off of existing circuits on back deck. All wiring was ran in conduit to protect from weather and physical damage. A customer-supplied GFCI receptacle was installed in pantry at existing location where a blanked junction box was.
Tech John diagnosed pool lights not working. A GFCI receptacle was found to be powering the timer for the lights and was tripped. Due to the age of the receptacle and the fact that is was found tripped, it was replaced as a minor repair included in the diagnosis. Once power was restored to the lights, some came on while others didn't. Homeowners stated they hadn't worked in over 8 years, so they decided to look for replacement lights and were given a quote to replace them.
Troubleshooting a 150 amp main breaker tripping. Found breaker box to overloaded causing breaker to trip. Recommend upgrading electrical service.
Installed fan installed fan rated breaker box
Replacing three way switches