Mr. Value Electricians has provided the electrical services for Gainesville GA—from ceiling fan installation to breaker box replacement and electrical shorts—for years.
Call us now at: (770) 894-1566 or check out why your neighbors rely on us to deliver electrical services at great value for a fair price in Gainesville GA.
for Gainesville, GA
Our Reviews by City
Excellent very happy
Janice - Gainesville, GA 30506
He was awesome!!!
Ray - Gainesville, GA 30506
Great job will definitely use you guys again friendly tech
Melissa - Gainesville, GA 30506
Did a great job and got the job down quick
Julie - Gainesville, GA 30506
Quick diagnosis and Repair
Winnie - Gainesville, GA 30506
John was able to quickly diagnose a open wire within a closet light outlet which could have taken much longer as the storm knocked out 4 walls worth of outlets, lights and fans.
Great service, great company!
Sally - Gainesville, GA 30501
Cole was very friendly and knowledgeable. He was very clear in his explanation of the work he thought needed done on my electrical system. Very happy with his work.
Mark - Gainesville, GA 30506
James - Gainesville, GA 30506
Very professional. Dock safest it's been in years.
Awesome job! I would like Cole as my Electrician.Fast , and listens to what I wanted.
Paula - Gainesville, GA 30506
Great Service, No Surprises
Brian - Gainesville, GA 30506
We had Clay and Cole both do some work in our home and they did a great job. Both were on time and friendly. They also cleaned up behind themselves which was refreshing. I would highly recommend Mr. Value for your electrical needs.
Came out on a Satuday, Thanks!
Jay - Gainesville, GA 30506
Professional & Courteous
May - Gainesville, GA 30506
On time, accurate estimate, clean, courteous, professional job
Way above and beyond
Teresa - Gainesville, GA 30501
What should have been a simple installation turned into a fairly major electrical service. Clay kept me informed and tried to make sure I understood what he was doing. I didn't, but I pretended to. Oh and he came out within a few hours of my call because i think the company suspected that my problem could be dangerous.
Michele - Gainesville, GA 30506
Mark was great! Professional, timely and fixed the breakers for me.
Wendy - Gainesville, GA 30506
Electrician diagnosed a power issue with the master bedroom, outlets and master bathroom lights, not working. Electrician found that a loose connection in the outlet to the right of master bed was causing the power outage issue. Electrician replace the outlet to correct the issue.
Diagnosed lights flickering, Fixed stabbed in receptacles that was causing power to master bed and bath to flicker.
Installation of lights
Installing multiple fixtures and ceiling fans
Making repairs per an electrical inspection.
Diagnosing Christmas lights tripping
Electrician Cole Jones installed 2 new ceiling fans and replaced the existing fiberglass boxes with ceiling fan weight rated boxes. Installed new switch and wiring for 2 new flood lights for back yard. Relocated a kitchen table chandelier to center over table
Deck outlet rewiring, vanity lights on n bathrooms, whole house surge protector and electrical system inspection
Tech John installed 50-amp wiring for new Tesla charger in garage. Power was pulled from meter base, ran in conduit, and directly wired into wall-mounted Tesla charger.
Tech John replaced faulty 15-amp dual function BR breaker for disposal.
Tech John installed ceiling fan on existing fan rated box in living room, installed a chandelier in dining room, installed a pendant light in the hallway/foyer, and installed new wiring for a TV receptacle above the fireplace in living room.
Diagnosing burnt dryer outlet
Installing outdoor rated fans and diagnosing a circuit
Tech John installed customer-supplied car charger, new 50-amp rated wiring ran in PVC conduit where needed, and a 50-amp breaker in the meter disconnect. The charger was tested and verified to be functioning properly after installation.
Boat dock inspection
Trouble shoot Air B&B
Tech John diagnosed multiple outlets with no power. The issue was determined to be a loose connection in a lighting outlet junction. The issue was corrected, power was restored, and the circuit was verified to be working properly after the repair.
Installing new wiring for a 20 amp three phase circuit for a welding machine.
Tech John diagnosed issue with upstairs bedroom tripping. The issue was determined to be an improperly wired switch box that had shorted the hot and ground conductors, causing the breaker to trip. The issue was corrected, power was restored, and the circuit was verified to be operating properly.
-installed a new 20 amp circuit for refrigerator on a 20 amp dual function breaker and tied existing circuit through to next outlet inside refrigerator outlet box -diagnosed a tripping breaker and open neutral issue with the kitchen outlets left of refrigerator and in island and found that a loose neutral connection on the outlet left of refrigerator had caused the outlet the burn and become intermittent and trip the breaker -replaced the outlet and breaker to correct the issue -diagnosed a tripping breaker for the disposal circuit and found no loose connections in the circuit -replaced the breaker to correct the issue -installed a Cutler Hammer CH plug-on whole house surge protector -tightened all connections in electrical panel and tested all breakers with test buttons
Tech John installed new fan rated box to replace existing plastic light box that had broken under the weight of a ceiling fan. The existing fan was reinstalled as a courtesy.