Mr. Value Electricians has provided the electrical services for Decatur GA—from ceiling fan installation to breaker box replacement and electrical shorts—for years.
Call us now at: (770) 894-1566 or check out why your neighbors rely on us to deliver electrical services at great value for a fair price in Decatur GA.
for Decatur, GA
Our Reviews by City
Great service, skilled technician
Miller - Decatur, GA
Cole Jones installed 2 fans. Very skillful, thoughtful, a really good listener. The best!
Casey - Decatur, GA
Cole Jones is an asset to your company. Not only did he find the problem immediately, he went over and beyond to correct it!
Melissa - Decatur, GA
We had Cole from Mr Value do some work to upgrade our wiring and he did a great job! He worked efficiently, was extremely polite and personable and the estimate was exactly what we paid!
Great service, installer helpful
Miller - Decatur, GA
Norma - Decatur, GA
Nice guy. Good job. Reasonably priced.
Finally Found the Right Company
John - Decatur, GA
After a disappointing experienced with Mr. Electric I called for the services of Mr. Value. Mark, the tech, was on time, knowledgeable, friendly, and fast. He found the issue, replaced the damaged wires, and installed my kitchen light- all for less than Mr. Electric.
Service with Value
Brian - Decatur, GA
Quick response, professional and ethical staff that provided cost effective service meeting expectations and delivering a great outcome.
Leon - Decatur, GA
Prompt, knowledgeable, fair price, answered all questions, completed job in a timely fashion.......what more do you want???? Highly recommended.
William - Decatur, GA
I had Mark install a chandelier, spotlight and rewire one four gang in my family room. He was extremely respectful and courteous as well as very knowledgeable and worked very fast. I would highly recommend them.
George - Decatur, GA
Excellent Customer Service and Very Professional
Michelle - Decatur, GA
Extremely professional and top notch customer service. I received a 30 minute window for arrival (amazing) and he arrived on time fully prepared. I would high recommend this company for smaller jobs like installing this ceiling fan, or something larger, which we are planning for in the future.
Efficient, Professional and Fairly-Priced
Mrs. Clarke - Decatur, GA
The electrician (Mark) fixed everything in a relatively short amount of time. He was very efficient, discovering the problem quickly and offering a flat-rate for service and parts that was not only fair, but also came with a lifetime guarantee. I am very pleased!
Mellissa - Decatur, GA
Chris was professional, knowledgeable and courteous! He explained everything, including pricing before starting any work. He made sure we understood what needed to be done and that all of our questions were answered with a clear, easy-to-understand explanation. We're going to recommend Mr. Value to all of our neighbors!
Arrived on time. Informative and shared knowledge. Completed project to customers satisfaction.
Keith - Decatur, GA
Did a good job in short amount of time.
Jack - Decatur, GA
Diagnosis and repair of GFCI outlet in Decatur
Installation of ceiling fans in Atlanta
installed new 110 volt 15/20 amp outlet
installed ceiling fan.
Replacing switches and GFCI outlets.
Installation of a chandelier in Atlanta
Installation of a 50 amp range circuit and a 20 amp dining room outlet circuit in Decatur
Changing out dryer outlet
Diagnosing breakers tripping
replaced standard bath fan motor
install recessed can lights
install toggle dimmer switch
Installing a 30 amp circuit for a car charger.
Replace breaker box and install grounding system.
Retrieving and installing ceiling fan as a replacement in sunroom.
Troubleshooting kitchen light not working. Found faulty wire taps in light box and repaired.
Installing an additional switch to separate bath light from vent fan.
Installing GFCI receptacles and correcting stray voltage
Inspected house due to loss of partial power and discovered surging on one phase coming from power company. Called GA power for resolution.
Bond screw in panel found to be stripped out. Rebounded neutrals to grounds in main breaker 100A panel to correct for improper voltages.
Installing new grounding system and running new ground wire into panel to ground previously ungrounded electrical sysyem